Fresh air environmental control hot water integrated machine
Layout plan of fresh air environmental control unit
The equipment is in the passive building to consume low energy consumption, realize fresh indoor air, heat (cold) recovery, constant temperature dehumidification and use the waste heat of the equipment to heat sanitary hot water.
It greatly reduces the energy consumption demand of building heating and refrigeration.
Parameters of fresh air environmental control hot water integrated machine
|Standard fresh air volume(m³h)||150||200||150||200||300||300|
|Supply air volume(m³/h)||500||800||500||800||1200||1200|
|Refrigeration heat exchange rate(%)||75||74||75||74||75||75|
|Heating heat exchange rate(%)||82||81||82||81||82||82|
|Hot water production rate(L/H)||100||150||100||150||200||200|
|Rated refrigerating power(w)||1180||1700||1180||1700||2400||2400|
|Heating rated power(W)||1310||1800||1310||1800||2650||2650|
|★Hot water production rate: the hot water working condition is measured at 20 ℃ and the water temperature rises from 15 ℃ to 55 ℃|